Contenu

Introduction

Conditions préalables

Conditions requises

Components Used

Conventions

Tableau des caractéristiques d'alimentation

Informations connexes

Introduction

Ce document fournit les spécifications d'alimentation pour la plate-forme de provisionnement multiservice (MSPP) ONS 15454 de Cisco.

Conditions préalables

Conditions requises

Aucune spécification déterminée n'est requise pour ce document.

Components Used

Les informations de ce document sont basées sur le MSPP ONS 15454 de Cisco.

The information in this document was created from the devices in a specific lab environment. All of the devices used in this document started with a cleared (default) configuration. If your network is live, make sure that you understand the potential impact of any command.

Conventions

Pour plus d'informations sur les conventions utilisées dans ce document, reportez-vous à Conventions relatives aux conseils techniques Cisco.

Tableau des caractéristiques d'alimentation

Carte

Consommation électrique approximative

Niveaux de lumière de la fibre

AMPS

Watts

BTU par heure

Niveau Rx

Niveau Tx

Maximum. Dessin avec cartes

22.63

1088.64

3714.59

PLATEAU THERMOVENTILATEUR: AFC2

1.21

58.00

198.00

PLATEAU THERMOVENTILATEUR: FTA3-T

1.98

95.00

324.00

XC

0.28

13.00

46.00

XCVT

0.72

34.40

117.46

XC10G

1.64

78.60

268.40

TCC

0.20

9.82

33.53

TCC+

0.20

9.82

33.53

AIC

0.12

6.01

20.52

AIC-I

0,17

8.00

27.30

DS1-14

0.26

12.60

43.02

DS1N-14

0.26

12.60

43.02

DS3-12E

0.79

38.20

130.43

DS3N-12E

0.79

38.20

130.43

DS3XM-6

0.42

20.00

68.00

EC1-12

0.76

36.60

124.97

E100T-G

1.35

65.00

221.93

E1000-2-G avec GBIC

1.11

53.50

182.67

G1000-4 avec GBIC

1.31

63.00

215.11

Max. - min.

Max. - min.

OC3IR4-1310

0.40

13.20

65.56

-8 à -28

-8 à -15

OC12IR-1310

0.23

10.90

37.22

-8 à -28

-8 à -15

OC12LR-1310

0.25

9.28

41.00

-8 à -28

+2 à -3

OC12LR-1550

0.19

9.28

31.68

-8 à -28

+2 à -3

OC12IR4-1310

0.58

28.00

100.00

-8 à -30

-8 à -15

OC48IR-1310 à grande vitesse

0.67

32.20

109.94

0 à -18

0 à -5

OC48LR-1550 haute vitesse

0.56

26.80

91.50

-8 à -28

+3 à -2

OC48IR-1310 N'importe quel logement

0.77

37.20

127.01

0 à -18

0 à -5

OC48LR-1550, tout logement

0.77

37.20

127.01

-8 à -28

+3 à -2

OC48ELR-ITU 100 GHz

0.65

31.20

106.53

-9 à -27

0 à -2

OC48ELR-ITU 200 GHz

0.65

31.20

106.53

-8 à -28

0 à -2

OC192LR-1550

1.50

72.20

246.52

-10 à -19

+10 à +7

Informations connexes

- Catalogue de produits Cisco ONS 15454

- Présentation du produit : Cisco ONS 15454

- Fiche technique : Cartes d'interface Ethernet Cisco ONS 15454

- Fiche technique : Carte TCC+ Cisco ONS 15454

- Support et documentation techniques - Cisco Systems