Inhoud

Inleiding

Voorwaarden

Vereisten

Gebruikte componenten

Conventies

Maximaal energieverbruik van ONS 15454 MSPP

NEBS3/NEBS3E

ANSI

Maximale thermische lading

NEBS3/NEBS3E

ANSI

Gerelateerde informatie

Inleiding

In dit document worden het totale energieverbruik en de maximale thermische belasting van het ONS 15454 SONET multiservice provisioningplatform (MSPP) beschreven. Dit document verklaart ook het energieverbruik van de apparatuur en geeft informatie om een mogelijke stroomuitval te kunnen plannen.

Voorwaarden

Vereisten

Er zijn geen specifieke vereisten van toepassing op dit document.

Gebruikte componenten

De informatie in dit document is gebaseerd op de volgende software- en hardware-versies:

- Cisco ONS 15454 MSPP met NEBS3/NEBS3E-chassis

- Cisco ONS 15454 MSPP met ANSI-chassis

- Cisco ONS 15454 MSTP-module

De informatie in dit document is gebaseerd op de Cisco ONS 15454 handleiding, release 4.6 en Cisco ONS 15454 handleiding, release 6.0.

De informatie in dit document is gebaseerd op de apparaten in een specifieke laboratoriumomgeving. Alle apparaten die in dit document worden beschreven, hadden een opgeschoonde (standaard)configuratie. Als uw netwerk live is, moet u de potentiële impact van elke opdracht begrijpen.

Conventies

Raadpleeg Cisco Technical Tips Conventions (Conventies voor technische tips van Cisco) voor meer informatie over documentconventies.

Maximaal energieverbruik van ONS 15454 MSPP

Hier is het maximale stroomverbruik voor het NEBS3/NEBS3E chassis:

863.85 Watts w/ 2 TCC, 2 XCVT, 1 AIC, 2 OC48 IR 1310 HS, 10 E100T-12

Hier is het maximale stroomverbruik voor het ANSI-chassis:

1106.60 Watts w/ 2 TCC2, 2 XC10G, 1 AIC-I, 2 OC192 LR/STM64 LH 1550, 10 E100T-G

Tabel 1 - Stroomverbruik per kaart

Stroomverbruik bij benadering

Lichtniveau vezel

*******KAART***********

AMPS

Watts

BTU/uur

Rx-niveau

TX-niveau

ANSI: Max. Tekenen met kaarten

23.05

1106.60

3775.87

NEBS3/NEBS3E: Max. Tekenen met kaarten

18.00

863.85

2947.58

VENTILATOREENHEID: VET

1.14

55.00

187.67

VENTILATOREENHEID: VET2

1.21

58.00

198.00

VENTILATOREENHEID: VET3-T

1.98

95.00

324.00

XC

0.60

29.00

99.00

XCVT

0.72

34.40

117.46

XC10G

1.64

78.60

268.40

XC-VXC-10G router

1.4

67.00

288.62

TCC

0.20

9.82

33.53

TCC+

0.20

9.82

33.53

TCC2

0.54

26.00

88.80

TCC2P

0.56

27.00

92.2

AIC

0.12

6.01

20.52

AIC-I (incl. AEP)

0.17

8.00

27.30

DS1-14 en DS1N-14

0.26

12.60

43.02

DS1/E1-56

0.76

36.00

124.97

DS3-12 en DS3N-12

0.79

38.20

130.43

DS3/EC1-48

0.58

30.00

95.6

DS3-12E en DS3N-12E

0.56

26.80

91.51

DS3i-N-12

0.63

30.00

102.4

DS3XM-12-transceiver

0.71

34.00

116.1

DS3XM-6

0.42

20.00

68.00

EG1-12

0.76

36.60

124.97

FC_MR-4

1.25

60.00

212.00

E100T-12 en E100T-G

1.35

65.00

221.93

E1000-2 en E1000-2-G (incl. GBIC’s)

1.11

53.50

182.67

G1000-4 en G1K4 (inclusief GBIC’s)

1.31

63.00

215.11

CE-100T-8

1.10

53.14

181.3

ML100X-8

1.35

65.00

221.93

ML100T-12

1.10

53.00

181.00

ML1000-2

1.02

49.00

167.30

MAX. - MIN

MAX. - MIN

OC3 IR/SH 1310

0.40

19.20

65.56

-8 t/m -28

-8 t/m -15

OC3 IR/STM1SH 1310-8

0.48

23.00

78.50

-8 t/m -28

-8 t/m -15

OC12 IR/STM-4 SH 1310 switch

0.23

10.90

37.22

-8 t/m -28

-8 t/m -15

OC12 LR/STM-4 LH 1310

0.25

9.28

41.00

-8 t/m -28

+2 t/m -3

OC12 LR/STM-4 LH 1550 router

0.19

9.28

31.68

-8 t/m -28

+2 t/m -3

OC12 IR/STM-4 SH 1310-4 switch

0.58

28.00

100.00

-8 t/m -30

-8 t/m -15

OC48IR-1310 snelle WAN-interfacekaart

0.67

32.20

109.94

0 tot -18

0 tot -5

OC48LR-1550 snelle WAN-interfacekaart

0.56

26.80

91.50

-8 t/m -28

+3 t/m -2

OC48 IR/STM-16 SH AS1310

0.77

37.20

127.01

0 tot -18

0 tot -5

OC48 LR/STM-16 LH AS1550

0.77

37.20

127.01

-8 t/m -28

+3 t/m -2

OC480-ITU 100 GHz

0.65

31.20

106.53

-9 t/m -27

0 tot -2

OC480-ITU 200 GHz

0.65

31.20

106.53

-8 t/m -28

0 tot -2

OC192 SR/STM-64 OC-1310

0.98

47.00

160.50

-1 t/m -11

-1 t/m -6

OC192 IR/STM-64 SH 1550 switch

1.04

50.00

170.70

-1 t/m -14

+2 t/m -1

OC192 LR/STM-64 LH 1550 router

1.50

72.20

246.52

-10 tot -19

+10 tot +7

OC192 LR/STM-64 LH ITU 15xx.xx

1.08

52.00

177.60

-9 t/m -22

+6 t/m +3

OC192SR1/STM-64IO-glasvezelkaart met klein bereik en OC-192/STM-64 bereik voor elk bereik[1]

0.83

40.00

136.49

Specificaties SFP, XFP en GBIC

15454_MRC-12

0.79

38.00

129.66

Specificaties SFP, XFP en GBIC

TXP_MR_10G

0.73

35.00

119.50

Zie Documentatie

TXP_MR_10E

Nominaal 1,11 Maximum 1,04

Nominaal 40 Maximum 50

Nominaal 136,6 Maximum 170,7

Zie Documentatie

MXP_2,5G_10G

1.04

50.00

170.70

Zie Documentatie

MXP_2,5G_10E

Nominaal 1,11 Maximum 1,04

Nominaal 40 Maximum 50

Nominaal 136,6 Maximum 170,7

Zie Documentatie

MXP_MR_2.5G en MXP_MR_2.5G

Nominaal 1,04 Maximum 1,25

Nominaal 50 Maximum 60

Nominale 170,7 Maximum 204

Zie Documentatie

TXP_MR_2.5G en TXP_MR_2.5G

0.73

35.00

119.50

Zie Documentatie

OSCM

Nominaal

0.48

23.00

78.48

Zie Documentatie

Maximaal

0.54

26.00

88.71

OSC-CSM

Nominaal

0.50

24.00

81.89

Zie Documentatie

Maximaal

0.56

27.00

92.12

OPT-PRE

Nominaal

0.56

30.00

102.36

Zie Documentatie

Maximaal

0.81

39.00

133.07

OPT-BST

Nominaal

0.63

30.00

102.36

Zie Documentatie

Maximaal

0.81

39.00

133.07

32 MUX-O

Nominaal

0.33

16.00

54.59

Zie Documentatie

Maximaal

0.52

25.00

85.30

32 DMX-O

Nominaal

0.33

16.00

54.59

Zie Documentatie

Maximaal

0.52

25.00

85.30

32 DMX

Nominaal 0,31 Maximum 0,52

Nominale 15 Maximum 25

Nominaal 51.21 Maximum 85

4MD-xx.x

Nominaal

0.35

17.00

58.00

Zie Documentatie

Maximaal

0.52

25.00

85.30

AD-1C-xx.x

Nominaal

0.35

17.00

58.00

Zie Documentatie

Maximaal

0.52

25.00

85.30

AD-2C-xx.x

Nominaal

0.35

17.00

58.00

Zie Documentatie

Maximaal

0.52

25.00

85.30

AD-4C-xx.x

Nominaal

0.35

17.00

58.00

Zie Documentatie

Maximaal

0.52

25.00

85.30

AD-1B-xx.x

Nominaal

0.35

17.00

58.00

Zie Documentatie

Maximaal

0.52

25.00

85.30

AD-4B-xx.x

Nominaal

0.35

17.00

58.00

Zie Documentatie

Maximaal

0.52

25.00

85.30

32 WSS

Nominaal 1,04 Maximum 1,35

Nominaal 50 Maximum 65

Nominaal 170 Maximum 221

NEBS3/NEBS3E

Neem bijvoorbeeld een ONS 15454 die is uitgerust met NEBS3/NEBS3E chassis en deze configuratie:

- Twee kaarten voor timing, communicatie en controle+ (TCC+)

- Twee cross-connect-virtuele (XC-VT) kaarten

- Tien E100T-12 kaarten

- Twee OC48 IR 1310

- Eén AIC

Zo'n ONS 15454 heeft dit energieverbruik volgens normaal verbruik uit tabel 1:

(2 X 9.82W) + (2 X 34.40W) + (10 X 65.00W) + (2 X 32.20W) + 6.01W

= 806.85W + 55W (Fan tray) = 863.85W

ANSI

Neem bijvoorbeeld een ONS 15454 die is uitgerust met een ANSI-chassis en deze configuratie:

- Twee kaarten voor timing en controle 2 (TCC2)

- Twee cross-connect-10G (XC10G) kaarten

- Tien E100T-G-kaarten

- Twee OC192 LR/STM-64 LH 1550-modules

- Eén AIC-I

Zo'n ONS 15454 heeft dit energieverbruik volgens normaal verbruik uit tabel 1:

(2 X 26.00W) + (2 X 78.60W) + (10 X 65.00W) + (2 X 72.20W) + 8.00W

= 1011.60W + 95W (FTA3) = 1106.60W

Maximale thermische lading

Gezien het feit dat het ingangsvermogen uiteindelijk eindigt als warmte, gebruikt u deze formule om de maximale thermische belasting van de ONS 15454-schappen te bepalen:

Watts = BTUs/hr x 0.2930711 or BTUs/hr = Watts / 0.2930711

De thermische belasting op een volledig geladen plank varieert op basis van de kaarten in de plank en hun energiebehoeften.

NEBS3/NEBS3E

Volgens de specificaties in het gedeelte NEBS3/NEBS3E kan het enkele ONS 15454 NEBS3-chassis maximaal 863,85 watt vermogen vereisen. Op basis van de gegeven formule bedraagt de maximale thermische belasting van één enkel ONS 15454 NEBS3-chassis 2947,58 Basis Transmission Units (BTU's) per uur (afgerond op de tweede plaats).

ANSI

Volgens de specificaties in het ANSI-gedeelte kan voor één ONS 15454 ANSI-chassis een maximum van 1106,60 watt aan stroom nodig zijn. Op basis van de gegeven formule bedraagt de maximale thermische belasting van één enkel ONS 15454 ANSI-chassis 3775,87 BTU's per uur (afgerond op de tweede plaats).

Gerelateerde informatie

- ONS 15400 Series ondersteuningspagina

- Ondersteuning voor optische netwerkproducten

- Ondersteuningspagina voor optische technologie

- Technische ondersteuning en documentatie – Cisco Systems